1900ASG - FIRE-RATED ADJUSTABLE LOUVER WITH SECURITY GRILLE
Door Louver with Fusible Link activated at 165 Degrees F that is Listed by UL and WHI. Ideal for Use in Fire Doors with up to 1-1/2 Hour Rating for Security & Detention Applications. Drilling Holes in the Door for Installation is not Required.
Material: 18 gauge CRS frame. Min size 10" x 6", Max 24" x 24"
Louver: Z-blade louvers riveted to operating bar and 1-9/16" deep frame at 1" intervals. Mechanical stop holds blades open.
Frame & Grille: Mitered and welded corners. 12 gauge security grille welded to louver core with 13/16" square openings 1" on center, screws fastened through prepared frame into louver core; this mounting method leaves corridor side of frame free of fasteners for aesthetic and security purposes.
Operation: Adjustable blades of 16 gauge CRS pivot on cadmium-plated steel rivets. The blades are operated by a manual adjusting lever. A spring loaded fusible link mechanism is incorporated into the design; upon melting of the link, the action bar is actuated, thereby closing and locking all of the blades.
Door: for 1-3/4" steeel or composite door. Door cutout = order size
Fasteners: #8 x 3/4" Phillips flathead screws SMS.
Powder Coat Finishes: (B) Mineral Bronze (standard color), (G) Gray, (BK) Black, (FBK) Flat Black, (W) White, (SB) SC Beige, (SI) Silver, (S) Sand, (AB) AMS Beige, (R) Red, (GH) Gray Hammertone.
Free Flow Area: 45% free area
Fire door testing: CAN/ULC S104, NFPA252, UBC 7-2-94, UL10(b), UL10(c). Installed in accordance with NFPA-80. Louver size shall not exceed maximum width and height shall not be less than 10" and 6", respectively. Louvers may be provided for classified hollow metal type and composite type fire doors. Consult with the Local Authority Having Jursidiction (AHJ) to determine appropriate standards. Louver frame will be labeled with Listing mark.